The medical gas pipe system is designed to transport the medical gas from the gas station to the ward. It is consisted of the medical level degrease copper pipe, medical gas pressure regulator, medical gas alarm panel, area valve unit, installation fittings and accessories
The main oxygen pipeline and the branch pipeline into the room are used of defatted purple copper tube or stainless steel tube. The pipeline inside of bed head unit is using degrease copper pipe.
The gas riser pipe is designed in the pipeline well. Pipes should be piped when crossing the wall. The pipes installation should be neat and beautiful.
Pipe system using welded connection.
Metal seals throughout the pipe system connectionHorizontal pipe and branch pipe of bed head unit should be with maintenance valve.
Medical gas pipelines in medical rooms should be equipotential grounded; manifold/pipelines etc should be anti-static grounded.
Independent grounding resistance should less than 10Ω.
Pipeline Leakage Rate
Leakage test of medical gas pipelines when no terminal components are connected, the hourly leakage rate should not exceed 0.05%.According to Chinese standard GB50751-2012.